The mesh network SST2630 is a battery operated spread spectrum wireless remote/strap-on temperature sensor.
The sensor is encapsulated in a 0.25” OD 304 stainless steel probe (2” probe length) for single point pipe temperature monitoring.
Trs Systems mesh network Series 2000 wireless sensors utilize reliable Spread Spectrum Radio technology. They can be installed easily in minutes eliminating hundreds of feet of wire and saving installation cost while reducing installation labor risks.
The Series 2000 sensor Data-Link LED confirms the data transmission was received by the receiver for fast and reliable positioning of the sensor during installation. There is no need for special wireless installation equipment or tool.
Together with the Trs Systems Series 2000 receivers and controllers , the Trs Systems wireless sensors can be used with any LON, BacNet, MODbus, or DDC control system or panel.
The maximum radio transmission distance is dependent on building type. The maximum open air transmission distance is one mile. In a typical commercial building with steel I-beam construction, concrete floors with reinforcing rod, and metal stud walls, it can be expected that transmissions will penetrate vertically through floors and horizontally through 200 to 500 feet of walls, furniture and air.
Battery - One or two type 3.0V LiMNO2 1400 mAH (e.g. Duracell DL123A, Varta CR123A)
Probe length: 2”
Cable Length: 15 ft.
Housing : 1-3/4" X 3-1/8" X 5-3/4"
Temperature 0 to 125 deg F (Sensor Housing)
Humidity 5 to 95% RH non-condensing
Open Field Range:
One mile line of sight
25 to 125 deg F
0 to 200 deg F
-40 F to 160 deg F
Accuracy +/- 1 F
12 Bit Resolution
Center Transmit Frequency 923.58 MHz
Transmitter Power - 11 dB