The Series 2000 MODBUS network transceiver utilizes reliable Spread Spectrum Mesh network Radio technology. Together with other Trs wireless sensors and controls, the system can be used to transmit remote sensor readings, status/alarm indications and control signals wirelessly. It is compatible with any control systems or Programmable Logic Controller (PLC) panels that utilize MODBUS communication protocol or interface. Up to 50 separate physical wireless sensor transmitters and/or wireless remote output (analog & digital) modules can be used with one MOD9200D Transceiver and up to 100 data points and 100 outputs can be monitored and controlled with one (1) MOD9200 Transceiver.
The maximum radio transmission distance is dependent on building type. The maximum open- air transmission distance is one mile. In a typical commercial building with steel I-beam construction, concrete floors with reinforcing rod, and metal stud walls, it can be expected that transmissions will penetrate vertically through floors and horizontally through 200 to 500 feet of walls, furniture and air.
Generally a wireless system will cover at least three floors - one floor above and one floor below the transceiver location. In some buildings with favorable transmission characteristics the system may cover more floors.
24 VAC 60 Hz, 400 mA (nominal)
9 to 24VDC model, 400 mA (nominal)
8.8” x 4.7” x 2.25”
Temoerature 32 to 150 deg F
Humidity 5 to 95% non-condensing
Flame Retardant ABS Plastic (Black)
UL Flame Rating – 94-5VA
Ethernet – RJ45, Cat. 5 cable
RS485 – Twisted pair with shield
RS232 – Serial cable
Operating Frequency Channel 902 – 928 MHz
Receiver Sensitivity (avg. power) –110 dBm